Window AC / August 25, 2018 / Babette Arsenault
Have everything ready and laid out before you have unpacked. Have the screen removed from the window. Remember that these only work for windows that can be pulled up. Ones that crank out will not open wide enough nor will they have anything to hold the air conditioner steady. Open up the window as wide as it can go to give yourself a little extra room to work. It is helpful if you have someone there to push down the top sash when the time comes. Make sure the air conditioner is facing the right way. The front which should be inside the room should have the dials and the cord to plug into the wall.
When a small window unit for a large room is not enough a large unit for a small place is waste of money. So you should buy a window air conditioner appropriately based on your room space. For a space up to 350 square feet you would require 8000 BTUs. The number of BTUs grows proportionately according to your space. Window air conditioners have high-energy efficient ratios noise-free and when fitted properly cool an entire space very quickly. There are lots of types of window air conditioners from different companies available at different prices. Companies like Haier Kelon and Carrier have products starting from price ranges as low as $50-$150. They come with quiet operation function timer dehumidification air filters and much more.
Window air conditioners came to the market as a solution for people who couldnt afford or did not want central air conditioning. Because central air conditioning can be quite expensive and because many people live in small apartments central air is not for everyone. This led to the advent of window air conditioners. Window air conditioners have a hot coil and a chilled coil along with two fans. The fans blow air over these coils and they in turn suck away the heat and humidity from the room into the outside area providing clean cool air. The capacity of an air conditioner is measured in BTUs. So the size of the air conditioner plays a vital role in determining its cooling capacity.